Carparking (Risk Group VP) shall be separate firecells.
Vehicles parked outside a building with part of the vehicle under a canopy. How far must the covering extend to make it a VP firecell?
I’ve considered 2m deep with the sides completely open to be OUTSIDE.
If it is deeper, longer (5 vehicle or more) and closed on one or both ends, it is INSIDE.
What does the SFPE community do to decide?
Is there a VP firecell in front of the restaurant in this photo?